NOTES : 
COMPLETER RAPPORTS POUR OLOFEE
-10 ET 11 JUILLET
-FAIRE FEUILLE DE REQUISITION POUR MATERIEL UTILISER CHEZ LES 
CLIENT 
PENDANT LA SEMAINE DU 8-11 JUILLET
-FAIRE RAPPORT POUR CLAIM DU 8-11 JUILLET


CLIENT A APPELER POUR QUELQUES PETITS TROUBLES MINEURS.
-UNE DES MODIFICATION CSA SERA A REVISER AVEC ENERGITEK.  ENLEVER 
FONCTIONEMENT DES RELAIS AIRFLOW POUR L\'INSTANT, LORS D\'UN 
EXTRACTION DE GRAIN LE SIGNAL EST PERDU ET ARRETE LE BRULEUR QUI 
ARRETE LE SYSTEME PAR LA SUITE.

-LE COMPRESSEUR DU CLIENT NE MAINTIENT PAS UNE PRESSION ASSEZ 
ELEVEE ET A TOUT LES 2-3 EXTRACTIONS VA PARTIR UNE ALARM \'\'LOW AIR 
PRESSURE\'\'.  JE CROIS LE CLIENT A PEUT ETRE REMPLACER LE BOYAUX 
D\'ALIMENTATION D\'AIR AVEC UN PLUS PETIT OU PLUS LONG, CECI DEVRA 
ETRE CORRIGER ET/OU AUSSI MODIFIER LA PRESSION MINIMALE DE SON 
COMPRESSEUR.

RECHERCHE ET DEVELOPPEMENT DU SOFTSTART POUR NOS PANNEAU EZ-
DRY.  A CREE LA PROGRAMMATION DU SYSTEM MODBUS RS485 ET AUSSI 
DE DETERMINER LES FONCTIONALITES QUE NOUS DESIRONS.  DE PLUS A 
VERIFIER SI ON PEUT DEMARRER LE SOFT START PAR MODBUS.

VEHICULES : 
