NOTES : 
DIAGNOSTIQUE ET CORRECTIONS
-REMPLACER CAP REGULATEUR MANQUANT
-VERIFICATION DU REGULATEUR BRULEUR 1 QUI \'\'SURGE\'\', NE SEMBLE PAS 
ETRE CRITIQUE, LA PRESSION JOUE D\'ENVIRON 2 A 3 PSI.
-VERIFIER GAUGE PRESSION, OK
-PURGER LIGNE LP POUR VOIR SI POSSIBLEMENT DE LA VAPEUR DANS 
LIGNE.
-REVERIFIER REGULATEUR, PRESSION JOUE DE LA MEME FACON.
-REMPLACER REGULATEUR POUR LA SATISFACTION CLIENT PRESSION OK 
(PIECE FOURNI PAR CASA ET DEVRAIS ETRE NO CHARGE AU CLIENT 
VERIFIER AVEC FGAUTHIER ETAIS DANS LE NON-INVENTORIER)
-AJUSTER START ON LOW FIRE POUR REMETTRE A 4 SECONDES ET NON 2 
SECONDES.
-VERIFIER EMPLACEMENT ROTOBINE OVERFLOW AVEC CLIENT, 
INSTALLATION EST CORRECT.
-REPONDRE AU QUESTIONS DU CLIENT ET DONNER QUELQUES CONSEILS 
AU NIVEAU DE L\'OPERATION ET SECHAGE DE GRAIN AVEC LE SECHOIR.
-LAISSER UN AIRFLOW SWITCH AU CLIENT NO CHARGE A LA DEMANDE 
FGAUTHIER (PIECE DE L\'INVENTAIRE DE SELECTRO)


VEHICULES : 

FACTURE # 427
