NOTES : 
APPEL DE SERVICE POUR TOPDRY PLC QUI A DES TROUBLES.

DIAGNOSTIQUE : ECRAN SEMBLE GELER ET SEULEMENT UN DES BRULEURS 
ALLUME.
-LA DATE DANS LE PLC ETAIS REGLER A 2099 CE QUI FAISAIS EN SORTE 
QU\'IL Y AVAIS DES PROBLEMES DE MEMOIRE CAUSANT LE SYSTEME A 
GELER. UNE FOIS CORRIGER CECI A ETE REGLER.
-LA CARTE 120 INPUT DU PLC NE FONCTIONNAIS PAS CORRECTEMENT 
DONC SELEMENT UN DES BRULEURS ALLUMAIS ET DONNAIS CONFIRMATION 
DE FLAMME.
-REMPLACER CARTE DANS PLC

*****

EFFECTUER FORMATION TOP DRY AVEC CLIENT

*****

PIECES A CLAIMER GSI
GT3-1652

*****
FACTURE # 400
FRAIS FIXE DIAGNOSTIQUE
TRANSPORT

VEHICULES : 
