NOTES : 
CLIENT A APPELER POUR DIRE QUE AUSSITOT IL PART SES BRULEURS DU SECHOIR IL TOMBE EN VAPOR HIGH LIMIT, IL FAUT BAISSER LES PRESSIONS A 7PSI ET MEME A CECI LES VAPORISATEUR SONT BRULANTS.  LE CLIENT A MENTIONER QU\'IL VENAIS JUSTE DE FAIRE REMPLACER SA TANK DE PROPANE PAR UN NOUVEAU FOURNISSEUR.

SUR PLACE APRES QUELQUES VERIFICATIONS IL ETAIS CONFIRMER QUE LA COMPAGNIE DE PROPANE A RACCORDER SA TANK DE PROPANE EN VAPEUR EN NON EN PROPANE LIQUIDE CE QUI CAUSE UN MAUVAIS FONCTIONEMENT AVEC LE SECHOIR.  LA COMPAGNIE DE PROPANE DEVRAIS PASSER ET CORRIGER LA SITUATION.

PIECES : 


VEHICULES : 
DEPART 12H55