NOTES :  VERIFICATION SEHOIR TOUR TM-1010 POUR REMISE A NEUF
BESOIN BRANCHEMENT PROPANE : CLIENT DOIS VERIFIER AVEC SON 
FOURNISSEUR

BESOIN BRANCHEMENT ELECTRIQUE DE PUISSANCE : CLIENT DOIS 
VERIFIER AVEC SON ELECTRICIEN

SUR LE SECHOIR
-BESOIN GAUGE 0-30 PSI
-BESOIN HI ET LOW GAS PRESSURE SWITCH (BARKSDALE)
-HI GAS PRESSURE DOIS ETRE DEPLACER AU BON ENDROIT
-CYCLE VALVE MANQUE LA SOLENOIDE (RAJOUT DU SOLENOID OU UPGRADE 
A VALVE MODULANTE A VERIFIER AVEC FGAUTHIER)
-BESOIN GAUGE 0-100WC
-DOIS ENLEVER LES BOITIER EXTRA POUR LES SONDES DE GRAINS.
-LES SONDES DE GRAIN EN BOITIER PVC, ON PEUT RECUPERER LES SONDES 
MAIS ON UPGRADE TU AVEC LES BOITIERS EN METALIQUE, PLASTIQUE 
SEMBLE FATIGUER.
-BOUCHER LES TROUS QUI SE TROUVE DANS LA SECTION DES SONDES DE 
GRAINS.
-A RAJOUTER UN BOITIER DE JONCTION SUR LA PASSERELLE POUR FAIRE 
LES CONNECTIONS DES SONDES DE GRAINS.  IL FAUT AUSSI PASSER DU 
FILLAGE POUR RELIER AU PANNEAU DE PUISSANCE
-BESOIN REMPLACER LES 3 HOSE FLEXIBLE POUR LE BRULEUR, CEUX QUI 
SONT EN PLACE SONT AVEC LA GAINE EN RUBBER QUI A EU UN RAPELLE 
DESSUS, DE PLUS CELUI DU BRULEUR SEBLE AVOIR ETE COCHER.
-BRULEUR, RECOMMANDE DE REMPLACER LA FLAME ROD PAR UN UV 
SENSOR.
-REMPLACER SPARK PLUG ET FILLAGE, A RAJOUTER BOITE JONCTION POUR 
LES CONNECTIONS AUSSI.
-TARP JAUNE TOPDRY POUR COUVRIR BRULEUR HORS SAISON?
-VAPORISATEUR A ETRE PEINTURER
-BOITIER DU OUTSIDE OVERHEAT AVAIS PRESENCE D\'EAU ET LES VIS POUR 
FERMER LE COUVERS SONT BRISER (3 SUR 4), RECOMMANDE REMPLACER 
AVEC UN KIT OUTSIDE OVERHEAT.  BESOIN AUSSI CABLE TECK POUR FAIRE 
CONNECTION AU PANNEAU PRINCIPALE
-BOITIER DE LA SONDE D\'HUMIDITE ENTREE, COUVERT NE FERME PLUS, 
DOIS REMPLACER LA BOITE DE JONCTION.
-ROTOBINE DE TOIT, A VERIFIER SI ON REMPLACE AVEC UNE ROTOBINE 
STYLE TOPDRY?
-PANNEAU DE CONTROLE A ETE LOCALISER A LA SHOP, BESOIN DE L\'ECRAN 
ET LA CARTE QUI S\'INSTALLE EN ARRIERE DE L\'ECRAN.
-PANNEAU DE CONTROLE DU CLIENT SERA INSTALLER EN DESSOUS DU 
CONIQUE COLLER SUR LE SECHOIR, VA AVOIR BESOIN DE FIL TECK ENTRE 
LES DEUX PANNEAU AINSI QUE LE CABLE ETHERNET.