NOTES : 
DEMARRAGE TOP DRY.  PERDU 3HRS SUR PLACE CAR LE FILL SYSTEME DE L\'ELECTRICIEN N\'ETAIS PAS FONCTIONEL ET CECI 
NOUS EMPECHAIS DE FAIRE 
FONCTIONNER LE SYSTEME AUTOFLOW.  ENSUITE BRULEUR #1 NE PARTAIS PAS, APRES AVOIR DIAGNOSTIQUER LE PROBLEME 
L\'ELECTRICIEN A MAL 
BRANCHER UN FIL DANS LE PANNEAU DU BRULEUR CE QUI A RETOURNER DU 120V SUR LE COTE NEUTRE DE LA SORTIE DE LA 
CARTE FENWAL.  J\'AI DU 
CORRIGER LE BRANCHEMENT DU FIL ET REMPLACER LA CARTE FENWAL CAR ELLE NE FONCTIONNAIS PLUS, EN PLUS D\'UNE 
PERTE DE UNE HEURE 
SUPPLEMENTAIRE A CAUSE DE CE TROUBLE.

A FACTURER EN EXTRA 4HRS MOD TECH SECHOIR
A FACTURER EN EXTRA LA CARTE FENWAL

PARTIR SECHOIR ET DONNER FORMATION PAR LA SUITE

PIECES : 

HF-4624-R


VEHICULES : 
QUITTER 21H20