NOTES : 
- REMPLACEMENT DU CONTACTEUR (CONT40A120V) POUR FAN 40HP AERATION 
SILO.  BRIS CAUSE PAR DISCONNECT TROP PETIT POUR PRENDRE LA CHARGE 
DU DEMARRAGE MOTEUR. INSTALLATION FAIT PAR NOUS.
- INSTALLATION BASE ET RELAIS (GT3-1164), (GT3-1161) POUR CONTACT 
120V DU CONTACTEUR REMPLACE (120V PLUTOT QUE 24V)

CONT40A120V, GT3-1164 ET GT3-1161 PROVENANT DE CAM-EXPVB


