NOTES : 
AUDIT DU TSSA

VISITER LES CLIENTS SUIVANTES

JEAN DANIEL KIRBY
-CLIENT A BESOIN RAJOUTER PROTECTION CONTRE VEHICULE AUTOUR DE 
LA 
TANK PROPANE, 
CLIENT AVISER.
-MANQUE TESTE PRESSION POUR LIGNE A GAZ, INSPECTEUR TSSA VA 
AVISER 
LA 
COMPAGNIE DE GAZ (STINSON)

TERRYLAND FARMS
-MANQUE TEST DE PRESSION POUR LIGNE A GAZ, INSPECTEUR VA AVISER 
CLOENT.

DONALD WYLIE.
-MANQUE TEST DE PRESSION POUR LIGNE A GAZ, INSPECTEUR VA AVISER 
COMPAGNIE DE 
GAZ (LEVAC)

SCOTT CAMPBELL
-FUITE DE GAZ SUR STATION DE EMBRIDGE AVANT LE COMPTEUR, FERMER 
STATION ET 
AVISER IMMEDIATEMENT EMBRIDGE POUR EFFECTUER REPARATION.

BYL FIELD FARMS
-MANQUE TEST DE PRESSION POUR LIGNE A GAZ, INSPECTEUR VA 
INFORMER 
COMPAGNIE 
DE GAZ (LEVAC)

HAGEN FARMS
-CLIENT A CONSTUIT UN ENCLOS AUTOUR DU BRULEUR... POURRAIS 
CADENASSER SYSTEME.

SILVERCREST FARM
-TOUT OK

PAUL VANDERWEILEN 
-CORRECTIONS A APPORTER SUR INSTALLATIONS A GAZ, INSPECTEUR VA 
AVISER CONPAGNIE

WANNA MAKE IT
-CORRECTION A APPORTER POUR TANK DU SECHOIR XTREME, INSPECTEUR 
VA 
AVISER 
COMPAGNIE

DOMAR FARM
-CORRIGER SUPPORTS POUR TUYAUX GAZ
-MANQUE COUVERT POUR REGULATEUR
-TAPE ELECTRIQUE SUR FITTINGS A GAZ
INSPECTEUR VA AVISER COMPAGNIE DE GAZ

QUITTER 19H10

VEHICULES : 
