NOTES :   APPEL POUR RAPPEL GSI AVEC LES RESISTANCES DE PRECISION 
POUR LES SONDES DE GRAIN TOP DRY PLC

SUR PLACE, LE RAPPEL A DEJA ETE FAIT... MAIS 2 SUR 4 SONDES NE LISENT 
PAS ET SONT ''DISABLED''.  A VERIFIER AVEC FGAUTHIER SI C'EST COUVERT 
PAR CASA OU CA DEVIENS UN APPEL DE SERVICE A FACTURER.
DIAGNOSTIQUE : 
-VERIFIER LES BRANCHEMENTS, IL Y AVAIS UNE MARETTE DE 
COMPLETEMENT LOOSE DANS LA BOITE DE JONCTION POUR LES SONDES DE 
TEMPERATURES CAUSANT LE TROUBLE AVEC UNE DES SONDES.  IL Y AVAIS 
AUSSI UN DES FIL MAL DEGAINER DANS LE BOITE DE JONCTION PLC 
CAUSANT UN TROUBLE AVEC LA DEUXIEME SONDE QUI NE FONCTIONAIS 
PAS.  LES 4 SONDES SEMBLE LIRE CORRECTEMENT.