NOTES : DIAGNOSTIQUE ET REPARATION SYSTEME TOP DRY AVEC 
BIOMASSE.
*****
VERIFIER SYSTEM ET ANALYSER BRANCHEMENT ENTRE SYSTEME BIOMASSE 
ET PLC TOPDRY
MANQUE LE SUIVANT POUR FONCTIONNER
-SIGNAL AUX CONTACT BRULEUR 1
-SIGNAL AUX CONTACT BRULEUR 2
-SIGNAL POUR FAN 1 CONTACTEUR TOUJOURS ALLIMENTER AU SYSTEME 
BIOMASSE
-SIGNAL POUR FAN 2 CONTACTEUR TOUJOURS ALIMENTER AU SYSTEME DE 
BIOMASSE
-SIGNAL POUR AIRFLOW 1, INPUT DU PLC EST BRANCHER AU INPUT SYSTEM 
BIOMASSE, AUCUN ENVOI DE SIGNAL
-SIGNAL POUR AIRFLOW 2, INPUT DU PLC EST BRANCHER AU INPUT SYSTEM 
BIOMASSE, AUCUN ENVOI DE SIGNAL

CORRECTIONS APPORTER.
-INSTALLATION RELAIS 120V2C POUR ISOLER LE SIGNAL FAN 1 
CONTACTEUR ENVOYER AU SYSTEME BIOMASSE, QUAND IL Y A DEMANDE DE 
VENTILATION LE SIGNAL PASSE PAR UN DES CONTACTS ET ENSUITE ENVOI 
LE SIGNAL AU SYSTEME BIOMASSE.  LE DEUXIEME CONTACT SERT POUR 
FAIRE UN SIGNAL MIRROIR POUR PROUVER AU TOPDRY PLC QUE LE 
CONTACT AUX EST ENCLENCHER.
-(MEME INSTALLATION POUR BRULEUR 2 AUSSI)

-INSTALLATION RELAIS 120V2C POUR ENVOYER SIGNAL DU AIRFLOW AU 
TOPDRY, IL EST ALIMENTER PAR LE PREMIER RELAIS 120V2C.  LE CONTACT 
PREND ENSUITE LE SIGNAL DU AIRFLOW SWITCH EN FONCTION ET L'ENVOI 
AU TOPDRY PLC ET AU SYSTEME DE BIOMASSE.
-(MEME INSTALLATION POUR BRULEUR 2 AUSSI)

LORSQUE BRULEUR A ETE ALIMENTER.  LA CARTE INPUT PLC 120V 2 
CONTACT S'EST MISE A BRULER.
-DIAGNOSTIQUE ET VERIFICATION DU CIRCUIT DEMONTRE QU'IL Y AVAIS 
PLUSIEURS ERREURS DE BRANCHEMENT.
-BRULEUR 2 : SIGNAL POUR BRULEUR BRANCHER SUR 24VDC
-BRULEUR 2 : CARTE DE BRULEUR BRANCHER SUR CONTACT POUR 
VENTILATEUR
-BRULEUR 1 :SIGNAL POUR BRULEUR BRANCHER AVEC FIL POUR 
VENTILATEUR
-SUR BRULEUR 1 : CARTE FENWAL ALIMENTER PAR THERMOSTAT BAS 
NIVEAU ET ENSUITE ALIMENTER DIRECTEMENT SUR 120VAC.

-LES BRANCHEMENTS ON TOUS ETE VERIFIER ET CORRIGER.
-ENSUITE REMPLACER CARTE BRULER DANS LE PLC

DIAGNOSTIQUE BRULEUR 1
-CARTE FENWAL, ROUILLER ET ENDOMMAGER, REMPLACER.
-RELAIS 24V1C, ENDOMMAGER, ROUILLER NE FONCTIONNE PLUS, 
REMPLACER.

SYSTEME FONCTIONNE BIEN.
-LAISSER CYCLER A BASSE TEMPERATURE 10-15 MIN SANS AUCUN 
PROBLEME. 
-LAISSER CLIENT SAVOIR TOUT EST FONCTIONEL.