NOTES : 
VERIFIER SECHOIR
-CORRIGER TROUBLE AVEC VALVE MODULANTE QUI NE FERME PAS QUAND ON 
ARRETE LE BRULEUR.
-VALVE MODULANTE ETAIS ALIMENTER SUR LA BORNE L1 AU LIEU DE 21, 
CORRIGER
-TROUBLE POUR RAMPE SUR CONTROLEUR DE TEMPERATURE OK, EXPLIQUER 
AU CLIENT.
-LAISSER METER POUR PRESSION STATIQUE AU CLIENT POUR QU\'IL PUISSE 
AJUSTER LES VENTILATEURS.
