NOTES :  AVEC SAMI AMEUR (DEPART CASA 10H30 RETOUR CHEZ CASA 
18H15
* * *APPEL DE SERVICE SYSTEM EZCONTROLE.* * *
QUAND IL Y A UNE ACTIVATION DE SEQUENCE AUSSITOT QUE LE 
CONVOYEUR PART, LES CONTACTEUR POUR L\'ELEVATEUR ET LE RELAIS 
DEMARRAGE POUR LE CONVOYEUR ACTIVE ET DESACTIVE DE FACON 
SPORADIQUE.

DIAGNOSTIQUE :

-VERIFIER TROUBLE POUR CONFIRMER PROBLEME
-FAIRE FONCTIONNER ELEVATEUR SEUL, ELEVATEUR FONCTIONNE OK
-FAIRE FONCTIONNER CONVOYEUR SEUL, CONVOYEUR FONCTIONNE OK.
-VERIFIER OUTPUT DU VFD CONVOYEUR, SEUL OUTPUT EST POUR UNE 
FAUTE, QUAND ACTIVER LE OUTPUT SIMULE UN OVERLOAD DE L\'ELEVATEUR 
DONC PAS LA SOURCE DU PROBLEME.
-VERIFIER LES INPUT DU VFD, IL Y A UNE DEMANDE DE \'\'RUN\'\' ET DES 
DEMANDES DE DIFFERENTES VITESSES.  SEMBLE TOUS FONCTIONNER 
COMME PREVU.
-DEBRANCHER RELAIS DU VFD POUR DEMANDE DE DEMARRAGE ET FAIRE 
UN DEMANDE DE TRANSFERT, LE TEMOIN DU RELAIS ACTIVE, ELEVATEUR 
FONCTIONE SANS PROBLEME.  LE TROUBLE SEMBLE ETRE LORSQUE LE VFD 
DU CONVOYEUR FONCTIONNE.
-VERIFIER LES PLANS ELECTRIQUES POUR VOIR SI QUAND LE CONVOYEUR 
FONCTIONNE, SI IL Y A UN CAPTEUR OU COMPTE TOUR QUI EST ACTIVER 
QUI POURRAIS ETRE PROBLEMATIQUE, AUCUN.
-FAIRE FONCTIONNER DE NOUVEAU SEULEMENT LE CONVOYEUR.  EN 
OBSERVENT LES ENTREES ET SORTIES DU PLC.  IL Y A DEUX ENTREES QUI 
SEMBLE ACTIVER DE FACON SPORADIQUES.
-DEBRANCHER TEMPORAIREMENT LES DEUX ENTREES, PROBLEME SEMBLE 
RESOLU.  VERIFIER LES DITES ENTREE, SESONT LE POSITIONS DES 
CULOTTES ELEVATEUR QUI NE SONT PAS SUPPOSER ETRE ACTIVER.  CECI 
DONNE UNE CONDITION IMPOSSIBLE D\'OUVERT ET FERMER EN MEME TEMPS 
CAUSANT LE TROUBLE.
-PASSER UN FILS SHIELDER TEMPORAIRE SUR UN DES CAPTEURS 
DIRECTEMENT DU CAPTEUR A L\'ENTREE SUR LE PANNEAU EZ-CONTROLE, 
PROBLEME SEMBLE SE RESOUDRE.
-INSTALLER RELAIS TEMPORAIRE POUR DESACTIVER LES DEUX CAPTEURS 
LORSQUE L\'ELEVATEUR EST EN FONCTION.
-IL VA FALLOIR PASSER DES FIL SHIELDER DE FACON PERMENANT POUR 
CORRIGER LE PROBLEME D\'INTERFERENCE.