NOTES : 
DRYER MASTER
-INSTALLER BOITIER ECHANTILLONNEUR SUR HOPPER D\'EXTRACTION DU 
SECHOIR LAW
-DETERMINER QUE LA PLAGE POUR LES EXTRACTIONS DEVRAIS SE SITUER 
ENTRE 0-40 EXTRACTIONS A L\'HEURE
-RACCORDER LE RATE OUT AU RATE IN DU DRYER MASTER
-CALIBRER LES COURBES POUR LE RATE IN/OUT DU DRYER MASTER
-REBRANCHER LE RATE IN/OUT AU SECHOIR LAW
-CALIBRER LA COURBE POUR LA TEMPERATURE PLENUM DU SECHOIR
-RACCORDER LE FIL 120VAC DIRECTEMENT A LA BOITE DE JONCTION POUR 
MOTEUR D\'ECHANTILLONEUR
-CONFIGURER LES ALARMES SUR LE DRYMASTER
-RACCORDER LA CONNECTION INTERNET AU DRYMASTER
-EN FONCTION LA SONDE DE SORTIE DE GRAIN TOMBAIS SOUVENT EN 
EMPTY, APRES AVOIR OBSERVER LE FONCTIONEMENT DU SECHOIR IL ETAIS 
DETERMINER QUE LE HOPPER D\'EXTRACTION SE FAISAIS TOUJOURS 
COMPLETEMENT VIDER ET CECI CAUSAIS LE GRAIN SUR LA SONDE A SE 
FAIRE ENLEVER PAR VACUUM.  AJUSTEMENT DES DELAIS POUR LE 
CONVOYEUR PAR PROCETECH.
-PROCETECH AVAIS FAIT SAUTER LA FUSIBLE PRINCIPALE DE 7A POUR LE 
CONTROLE DE LEUR PANNEAU PRINCIPALE, JE LUI AI FOURNI UNE 5A QUE 
JAVAIS EN STOCK POUR DEPANNER.
-PROGRAMMER LES SECTION SECHAGE/REFROIDISSEMENT AU DRYMASTER
-IMPOSSIBLE DE DETERMINER LE NOMBRE D\'EXTRACTIONS TOTAL POUR 
VIDER LE SECHOIR, NOUS AVONS DETERMINER QUE C\'EST POSSIBLEMENT 
83 EXTRACTIONS TOTAL BASSER SUR 50 TONNES CAPACITE TOTAL ET 
APPROX 600KG PAR EXTRACTION, PROCETECH N\'ONT PAS LES INFO, LAW NE 
SAVENT PAS ET LE CLIENT N\'EST PAS CERTAIN.  J\'AI AVISER LE CLIENT 
POUR BIEN FAIRE IL FAUDRAIS VIDER LE SECHOIR COMPLETEMENT PAR 
EXTRACTION ET COMPTER LE NOMBRE D\'EXTRACTIONS TOTAL.
-FORMER LE CLIENT SUR LE FONCTIONEMENT DU DRYMASTER, CECI INCLUS 
LE PERIODE DE RODAGE DE GRAIN, COMMENT AJUSTER LES PARAMETRES 
D\'ALARME, LE THROUGHPUT, CALIBRATIONS SONDES DE TEMPERATURE, LES 
RAPPORT D\'IMPRESSION, LE CONTROLE AUTO/MANUEL, L\'INTERFACE WEB, 
ETC, ETC.
-JE ME SUIS ASSURER LE CLIENT COMPRENDS TRES BIEN LE 
FONCTIONEMENT AVANT MON DEPART.

-AJUSTER LA PRESSION POUR LA PROBE DE GRAIN EN MODE AUTOMATIQUE 
(CECI A PRIS 5 MIN)

VEHICULES : 
16H40-17H05: GAZ/PROPANE CAMION.
0H30-1H00 : ARRET AU BUREAU, RAPPORTER MOTEUR 15HP DE STRYUK, 
RAPPORTER BOITIER POUR ECHANTILLIONEUR GRANT AG, LAISSER PIECES 
SUR BUREAU A VBOUCHER POUR FC GAUCHER, REMPLIR PROPANE CAMION.