NOTES : APPEL DE SERVICE TOUR TM-1015 ( DEMANDER PAR MLEVEILLER )
DIAGNOSTIQUE : LIGNE A GAZ GELE, PAS CAPABLE DE MONTER LA 
TEMPERATURE DU PLENUM.
-REMPLACER LES GAUGE A PRESSION DEFECT POUR VERIFIER LES 
PRESSIONS.
-DEMARRER SECHOIR, SECHOIR SEMBLE ROULER SUR LOW FIRE 
SEULEMENT.
-VERIFIER FILAGE, CONNECTEUR DIN POUR CYCLE SOLENOIDE CORRODER 
ET NE CONDUIT PLUS CORRECTEMENT.
-REMPLACER FIL POUR SOLENOID.
-SECHOIR A BIEN PARTI ET LIGNE NE GELE PLUS.
-ENLEVER RELAIS CYCLE QUI SEMBLE AVOIR ETE RAJOUTER DANS LE 
PASSER.