NOTES : 
****
TRAVAUX POUR COMPLETER DOSSIER CSA
(VERIFIER AVEC FGAUTHIER SI FACTURABLE AU CLIENT OU PARTI 
CONTRACT CASA)

**** AVEC MDION ET SAMI ****

VERIFICATION DU SECHOIR STRAHL POUR DETERMINER LES 
MODIFICATIONS A FAIRE POUR METTRE EN ORDRE ET PASSER APPROBATION 
CSA

-LPG EST BYPASSER ET PAS LE BON RANGE
-HPG DOIS ETRE REMPLACER PAR MANUAL RESET
-BRULER DEVRA ETRE AJUSTER LORSQUE LES MODIFICATIONS SERONT 
FAIT, RECOMMANDE D\'AVOIR EN MAIN LES SPRING POUR LES REGULATEURS 
BYPASS AINSI QUE POUR LE REGULATEUR PRINCIPALE
-LES VENT NE SONT PAS A 10\' DE L\'ENTREE D\'AIR IL DEVRONT ETRE 
RALLONGER.
-IL Y A BEACOUP DE BOUT DE TUYAUX EN ACIER NOIR QUI DEVRAIS ETRE 
PEINTURER SELON LE CODE.
-HTL (HI LIMIT CONTROLER) DOIS ETRE REMPLACER, MODELE NON 
CONFORME
-HTL DEVRAIS ETRE RELOCALISER DANS PANNEAU INTERIEUR
-BESOIN FIL SHIELDER TRIPLE, CONNECTEUR, BOITIER PVC POUR LA SONDE 
PT100 DU HTL
-DOIS RAJOUTER RELAIS DANS PANNEAU BRULEUR POUR CONTACT DU HTL 
(IL Y A SEULEMENT UN FIL SPARE DONC POSSIBILITE DE RAJOUTER UN 
RELAIS SINON TRES COMPLIQUE A PASSER FILLAGE ADDITIONEL)
-LES CIRCUIT ESTOP SONT TOUS BYPASSER ESTOP ET CAPTEURS DE 
PORTES (FILLAGE EST PAS RACCORDER DANS PANNEAU)
-QUELQUES CAPTEURS DE PORTES AURONT BESOIN ETRE ENLIGNER.
-A VERIFIER LE CICRUIT AVEC TIMER POUR LES UV SENSOR, IL Y A PEUT-
ETRE ERREUR DE BRANCHEMENT
-CLIENT DIT QUAND LE SECHOIR FONTIONNE ET SILO PLEIN LE MULTICO NE 
FAIS PAS ARRETER LE SECHOIR.  CECI A ETE CORRIGER SUR PLACE ET MISE 
A L\'ESSAI THEORIQUE.  RAJOUT DE LA BOUCLE \'\'CSE\'\' DU STRAHL AVEC UN 
CONTACT DE \'\'RSI\'\' (RELAIS SEQUENCE INTEROMPU) DU MULTICO.
-CLIENT EST VENU NOUS VOIR LORS DE LA VISITE ET AVAIS AUSSI POSER 
QUELQUES QUESTIONS SUR L\'OPERATION DU SYSTEME.
-ENLEVER CHAUFFE PANNEAU QUI ETAIS EN TRAIN METTRE LE FEU DANS 
PANNEAU EXTERIEUR.
-SELON SAMI IL FAUT PEUT-ETRE DECALLER LE TRAIN DE GAZ, A VERIFIER. 
