NOTES : AVEC SAMEUR    -  OUVERTURE DU CHANTIER

-NETTOYAGE DANS LE PANNEAU DE CONTROLE, ENLEVER FILLAGE NON-
ESSENTIEL
-SERRER TOUT LES BORNIERS DE FILLAGE PANNEAU CONTROLE ET 
PUISSANCE
-NETTOYAGE DES PANNEAU AVEC AIR COMPRIMER
-VERIFIER POUR REPARER LES CAPILAIRE HI LIMIT, IMPOSSIBLE D'ACCESS 
DE FACON SECURITAIRE EN ECHELLE, ACCESS NON/DANGEREUX ET REQUIS 
BEACOUP DE MAIN D'OUVRE POUR ETRE CAPABLE DE COMPLETER, NACELLE 
DE PREVU POUR COMPLETER CET PORTION DEMAIN AM
-REGULATEUR GAZ VENT SEMBLE ETRE INSTALLER A L'ENVERS, SERA 
VERIFIER DEMAIN AVEC NACELLE.
-REMPLACER LES SONDES DE TEMPERATURE POUR LE PLENUM ET HI LIMIT.
-REMPLACER AUSSI LA SONDE TYPE J POUR LE DRYERMASTER AVEC UNE 
SONDE PT100
-CONTACTER DRYERMASTER POUR AVOIR UN MODULE POUR PROGRAMMER 
LE OMEGETTE.
-INSTALLER CABARMCON (FOURNI PAR CLIENT) POUR ETRE CAPABLE 
BRANCHER LES SONDES AVEC LES 3 FIL (ETAIS SEULEMENT BRANCHER 
AVEC 2) ET POUR ACCOMODER LA SONDE DU DRYERMASTER AUSSI.
-ENLEVER VIEUX TUYAUX COPPE POUR BOITIERS AIRFLOW
-ENLEVER FILLAGE DANS BOITIER AIRFLOW
-RELOCALISER LES BOITIERS AIRFLOW DE FACON A NE PLUS AVOIR DES 
VIBRATION DE FAN
-RECABLER, ET IDENTIFIER LES BOITIER AIRFLOW.
-ENLEVER LES CABLES TECH QUI NE SERVIRONT PLUS POUR LES AIRFLOW
-ENLEVER LE CABLE DE THERMOCOUPLE TYPE J QUI NE SERVIRA PLUS
-DECONNECTER TEMPORAIREMENT PANNEAU SIEMENS POUR PERMETTRE DE 
PASSER FILLAGE ADDITIONEL
-VERIFIER LES RUN DE FIL POUR PLANIFIER ET PERMETTRE LE 
BRANCHEMENT DU SONDE POUR DRYERMASTER AINSI QUE LE FILLAGE 
POUR LES AIRFLOW.
-RAMASSAGE / NETTOYAGE DU CHANTIER AVANT DE PARTIR.