NOTES : 

CLIENT A DEMANDER UN APPEL DE SERVICE DUE AU PROXIMITÉ DE CHEZ GRAINS MJ.

IL DIT QUE LE GROS FEU EST BEAUCOUP TROP GROS ET QU\'IL EST IMPOSSIBLE D\'AJUSTER LE PETIT FEU.

PREMIÈRE CONSTATATION LE GUAGE DE PRESSION DE GAZ ÉTAIS DANS LA POSITION FERMER, DONC LE CLIENT CROYAIS QUE 
SON GROS FEU ETAIS AJUSTER A 15 PSI LORSQU\'EN RÉALITÉ IL ÉTAIS AJUSTER A 35-40 PSI.  LA PRESSION DES FEU A ÉTÉ 
AJUSTER CORRECTEMENT.  CLIENT A ÉTÉ AVISER DES CHANGEMENTS.

CLIENT N\'ETAIS PAS DISPONIBLE POUR ETRE SUR PLACE


VEHICULES : 
