NOTES : DEMARRAGE TOUR TM-1010     AVEC SAMI AMEUR

-FINALISATION DES DERNIERS RACCORDEMENTS.
-MISE A JOUR DU PROGRAMME DU SECHOIR.
-TESTER LES SYSTEMES.

TOUT FONCTIONNE SAUF QU'IL Y A DES PROBLEMATIQUES AVEC LE TRAIN 
DE GAZ.
-STRAINER BLOQUER.
-EAU ET BOUETTE DANS LES LIGNES A GAZ
-VALVE MAXXON IRRECUPERABLE ET DOIT ETRE REMPLACER.
-POSSIBLEMENT LA SOLENOIDE LP DOIS ETRE REMPLACER AUSSI.
****
NOTE LE FILL SYSTEM DU CLIENT N'EST PAS ENCORE FONCTIONEL, IL NE 
FONCTIONNE PAS EN SEQUENCE, LE CLIENT EST SUPPOSER FAIRE FAIRE LES 
CORRECTIONS NECESSAIRES A SON ELECTRICIEN.