NOTES : 
GATEWAY OPIBLUE :
MODULE GATEWAY SEMBLE AVOIR FAIT DEFAULT DE FACON 
SPECTACULAIRE, LE MODULE AVAIS DECLENCHER LE DISJONCTEUR DANS LE 
PANNEAU ELECTRIQUE DU CLIENT.
-VERIFIER LE MODULE GATEWAY, IL SEMBLE AVOIR EU UN ARC FLASH SUR 
LE MODULE, ET PRESENCE DE CARBONE ET PLASTIQUE FONDU SUR LE 
MODULE.
-VERIFIER FUSIBLES SUR LE MODULE, AUCUN FUSIBLE BRULEUR, CE QUI 
SEMBLE INDIQUER QU\'IL Y A UN OU PLUSIEURS COMPOSANTES A 
LINTERIEUR DU MODULE QUI ONT FAIT DEFAUT.

***VOIR FGAUTHIER POUR FACTURATION DE CETTE PIECE, JE CROIS 
SINCEREMENT QUE LA PIECE DEVRAIS ETRE REMPLACER SOUS GURANTIE 
DU MANUFACTURIER MEME SI IL SE FAIT DEJA QUELQUES ANNEES QUE LE 
CLIENT A SON SYSTEME.***

WATCHDOG EWON :
-INSTALLER MODULE EWON DANS LE PANNEAU EZ-CONTROLE
-INSTALLER ROUTER POUR PERMETTRE LE EWON DE FONCTIONNER AVEC UN 
MEME SOUS RESEAU QUE LE RESEAU DU CLIENT.  CECI PERMET AUSSI AU 
OPIBLUE D\'AVOIR UN ACCESS INTERNET.  (ROUTER A ETE PLACER DANS LE 
BOITIER OPIBLUE)
-CONFIGURER ROUTER ADDITIONEL POUR PERMETTRE LA COMMUNICATION 
ENTRE LE EWON ET LE ROUTER INTERNET DU CLIENT
-CONFIGURER LE EWON POUR FONCTIONNER AVEC UNE SOURCE INTERNET 
CABLE.
-CONFIGURER LE CELLULAIRE DU CLIENT POUR FONCTIONNER AVEC LE 
MODULE EWON

VEHICULES : 
DEPART 8H25