NARRIVER BUREAU: 6H05
DEPRT BUREAU: 6H20

PART DE BELAND A 9H00 RETOUR CASA 9H50-10H00 ARRIVE BELAND 11H00

CARTE SERIE 2000 FERME ALORS VERIFIER BOUTON ET BOUTON DEFECT ALORS ARRENGER SA
ENSUITE FUSIBLE SUR CARTE SERIE 200 SAUTER ALORS CHANGER LA FUSIBLE REFAIRE TESTE ET SAUTE ENCORE 
ALORS  CHANGER CARTE SERIE 2000 VOIR SI IL NES PAS SHORT AU GROUND ET NON LA FUIBLE SAUTE TOUJOURS 
VERIFIER QUOI QUI SORT DE LA CARTE DU COTER 120VOLT (COIL DU CONTACTEUR DE FAN)
    -DEBRANCHER FIL DU COIL DU CONTACTEUR DE LA FAN ET TOUTE SA FONCTION (CONTACTEUR DEFECT)
ALLER CHERCHER CONTACTEUR A SHOP ET CHANGER LE CONTACTEUR ET RESTER BRULEUR ET TOUTE ES OK 