NOTES : APPEL DE SERVICE, SYSTEME DE REMPLISSAGE NE FONCTIONNE PAS 
AVEC LES DEUX SECHOIRS.
* * * APRES DIAGNOSTIQUE* * *
-LE SECHOIR TOPDRY PLC ETAIS CONFIGURER AVEC 1 FILL SYSTEME, REMIS A 
2 POUR QU\'IL PUISSE CONTROLER ELEVATEUR ET VIS.
-CLIENT AVAIS COMPLETEMENT BYPASSER CONTACTEUR ELEVATEUR, 
REBRANCHER CORRECTEMENT.

-LE DEUXIEME SECHOIR EST INTERCONECTER AU VIS DE REMPLISSAGE MAIS 
NA PAS DE CONTROLE SUR L\'ELEVATEUR.  AVISER CLIENT QUE CECI POURRAIS 
ETRE CORRIGER DANS LE FUTUR MAIS N\'EMPECHE PAS LE BON 
FONCTIONNEMENT DU SYSTEME