NOTES :   SUIVI DU 6 NOV 2023
-INSTALLER THERMOMETRE POUR MESURER TEMP PLENUM, IL Y A UN ECART 
D'ENVIRON 30 DEGREE F
-REMPLACER SONDE PLENUM
-AUCUN CHANGEMENT
-REMPLACER CARTE RTD DU PLC
-ECART DE TEMPERATURE A ETE CORRIGER.
-SECHER QUELQUES BATCH ET PRISE D'ECHANTILLON
RESULTAT FINAL
PLENUM 160F
GRAIN TEMP 120 (AVEC OFFSET DE -20 LES 4 SONDES)
TEMPERATURE DE L'ECHANTILLON CORRESPOND AVEC LE GRAIN TEMP