NOTES : 
VERIFIER SECHOIR TOP DRY
-MANQUE CABLE RESEAU ETHERNET, ENTRE HMI ET AUTOMATE, RAJOUTER
-MOTEUR DE DRIVE POUR ACTUATEUR DES CHUTES ETAIS RENDU 
RACCORDER EN SENS INVERSE, CORRIGER
-TIGE POUR LIMITE SWITCH CHUTES, RENDU PLIER ET DEFORMER, 
REPLACER ET CORRIGER
-MANQUE JUMPER POUR GAS BRULEUR 1
-MANQUE FIL/FIL MALBRANCHER 24VCOMM ENTRE PANNEAU BRULEUR ET 
BOITE AUTOMATE.
-ENTREE 24V BRULER SUR CARTE DANS LE PLC POUR LOW LEVEL ROTARY 
SWITCH (PROBABLEMENT LORS DU TROUBLESHOOTING DU TECH 
PRECEDENT A PROBABLEMENT RACCORDER DU 120VAC), INTERCHANGER 
CARTE INPUT 1 AVEC LA CARTE INPUT 6 POUR RESSOUDRE MAIS IL A 
QUAND MEME UNE ENTREE DE BRULER (CARTE 6 SERT POUR DES INPUT SI 
LE CLIENT AURAIS 2 BRULEUR)
-AJUSTER PRESSIONS DE GAZ.
-FAIRE FORMATION AU CLIENT
