NOTES :  SERVICE CALL POUR VALVE MODULANTE TOUR SECHOIR.

-SAMEUR EN FORMATION (FACTURER SEULEMENT UN TECH, VOIR 
FGAUTHIER POUR FACTURATION AU BESOIN)

DIAGNOSTIQUE
-SUR LE DISPLAY I/O BOARD, LE JUMPER AUX1 N'ETAIS PAS A ON, CECI A 
COMME INCIDENCE QUE LE SYSTEME FONCTIONNE EN MODE HI/LOW ET 
NON AVEC LE SIGNAL 4-20MA DU MODUTROL.  EN HI LOW LE SIGNAL PASSE 
CONSTAMENT DE 0-100% FAISANT EN SORTE QUE LA CARTE MODUTROL 
PEUT EVENTUELLE SURCHAUFFER ET CESSER DE FONCTIONNER ET/OU 
AUSSI LE MOTEUR DE LA VALVE MODULANTE PEUT SURCHAUFFER ET/OU 
CESSER DE FONCTIONNER.

-REGLER AUX1 A ON, OBSERVER LE FONCTIONNEMENT DU SYSTEME, LA 
VALVE MODULANTE SEMBLE FONCTIONNER CORRECTEMENT ET DE FACON 
PLUS STABLE, LE CLIENT DIT QU'IL A REMARQUER UNE GROSSE 
DIFFERENCE.

-CORRIGER BRANCHEMENT POUR FILL SWITCH (AVEC NOUVEL ECRAN 
CHANGER L'AUTOMNE DERNIER)

-PARTI DINNER POUR LAISSER SYSTEME FONCTIONNER UN CERTAIN TEMPS, 
AU RETOUR DU DINNER TOUT FONCTIONNAIS TOUJOURS BIEN SUR LE 
SYSTEME.
****
DISCUTER AVEC CLIENT, SI IL Y A ENCORE DES TROUBLES AVEC LA VALVE 
MODULANTE APRES NOTRE VISITE, IL SERA A PREVOIR DE REMPLACER LE 
SETUP AVEC UNE VALVE SIEMENS.