NOTES : * * *  TRAVAUX POUR APPROBATION CSA * * *
-DEPART DE CHEZ CASA AVEC MDION 10H45
-ARRIVER CHEZ CLIENT 12H35
-INSTALLATION VALVE MANUELLE POUR CREE RESTRICTION AU MANIFOLD 
POUR PERMETTRE AU LOW GAS PRESSURE SWITCH DE FONCTIONNER
-REMPLACER HI GAS PRESSURE SWITCH PAR SWITCH MANUEL.
-TEST FIRE ET DIAGNOSTIQUE DU SYSTEM DE BRULEUR, IL Y A UN 
PROBLEMATIQUE AVEC LA VALVE POUR LE LOWFIRE BYPASS ELLE DEVRA 
ETRE REMPLACER.
-IL MANQUE UNE LIGNE DE RELEIF POUR LE VENT ENTRE LES DEUX POC
QUITTER CLIENT 16H00
-CHERCHER MATERIAUX NECESSAIRE POUR INSTALLER LE VENT, MAIS 
APRES PLUSIEURS MAGASIN RETOUR CHEZ CASA FAUTE D\'AVOIR LE 
NECESSAIRE DANS LES MAGASIN LOCAL PROCHE DU CLIENT.
-RAMASSER MATERIEL CHEZ PRO KONTROL POUR TRAVAUX /RETOUR CHEZ 
CASA 19H30