           * * *  APPEL DE SERVICE PAR FGAUTHIER * * *
DIAGNOSTIQUE
TOP DRY PLC
CONTACTEUR DE LA FAN #2 FONCTIONNAIS AUSSITOT QU\'IL Y AVAIS DU 
120V DANS LE PANNEAU. LE CONTACTEUR AVAIS ETE REMPLACER COMME 
PREMIERE APPROCHE.  UN TECH CASA A PASSER ET A CHANGER QUELQUES 
PIECES MAIS CA NA JAMAIS RESOLU LE PROBLEME.  LE CLIENT DIT QUE LA 
FAN A ARRETER DE FAIRE LE PROBLEME MAIS QUAND LE PANNEAU EST 
ALUMER IL RECOIT DES ALARMES DE FUITE A LA TERRE DE SA COMPAGNIE 
D\'ALARME.

-APRES AVOIR CHERCHER UN CERTAIN TEMPS IL A ETE DETERMINER QUE LE 
PANNEAU DE CONTROL POUR LE REMPLISSAGE QUI EST SUPPOSER DE 
FERMER UN CONTACT SEC POUR COMPLETER LA BOUCLE DE E-STOP POUR 
LE PANNEAU DU SECHOIR ETAIS MAL RACCORDER DE FACON QU\'IL Y AVAIS 
UN 120VAC EXTERNE QUI ETAIS INJECTER DANS LE SYSTEME.

-CECI AURAIS CREE LA FUITE A LA TERRE DETECTER PAR LE SYSTEME 
D\'ALARME DU CLIENT, AINSI QUE TRES PROBABLE LA CAUSE DU TROUBLE 
DE CONTACTEUR CAR LE 120VAC NE PARTAGE PAS LE MEME NEUTRE, IL EST 
POSSIBLE QU\'EN BACKFEEDANT LE 120V A TRAVERS LA MISE A LA TERRE 
QUE LE CONTACTEUR ENCLENCHE AVEC UN ASSEZ GRAND TENSION QUE LE 
CONTACTEUR ENCLENCHE.

-IMPOSSIBLE DE CONCLURE A 100% MAIS FORT PROBABLE LA CAUSE DU 
TROUBLE INITIAL.

******
NOTE
LE CLIENT DIT QUE QUAND LE TECH CASA EST PASSER QU\'IL AURAIS 
CHANGER UN DEUXIEME CONTACTEUR EN PLUS DE REMPLACER UNE CARTE 
D\'IGNITION.  LE CLIENT AURAIS AIMER RAVOIR SES PIECES D\'ORIGINE 
SURTOUT SI IL LUI ON ETE FACTURER. 
