NOTES : PROJET EZ CONTROLE TOPDRY
CHEZ Y AMIREAULT
-INTEGRER LES ALARMES POUR LES ALERTES.
-RACCORDER LE CONTROLE POUR LA FAN AERATION ET TESTER.
-INTEGRER LES DIFFERENTS TIMER SUR LA PAGE HMI
****
NOTE : POUR L'INTEGRATION DES DEUX FILL SYSTEME AVEC LE PANNEAU 
DU CLIENT IL VA FALLOIR PROBABLEMENT FACTURER DU TEMPS AU CLIENT 
POUR QUE CA PUISSE FONCTIONNER CORRECTEMENT.  CECI EST PREVU 
LORS DE LA PROCHAINE VISITE.
****
NOTE : 
-QUAND EFFECTUER UN TEST AVEC UN DES VENTILATEURS, IL Y A EU DES 
FUSIBLES QUI ONT BRULER ET UN CONTACTEUR DE FAN QUI AVAIS COLLER.
-ETE CHEZ CASA POUR CHERCHER UN CONTACTEUR DE REMPLACEMENT ET 
EFFECTUER REPARATION.
-PAR LA SUITE IL SEMBLE AVOIR UN PROBLEME AVEC LE FILLAGE DE 
PUISSANCE POUR LES DEUX BRULEURS.  F GAUTHIER A ETE AVISER
-IL VA FALLOIR PROBABLEMENT REPASSER DU NOUVEAU FILLAGE DE 
PUISSANCE POUR LES DEUX BRULEURS POUR ETRE CAPABLE DE FAIRE 
FONCTIONNER.
-FGAUTHIER EST SUPPOSER VERIFIER AVEC LE CLIENT POUR PROCEDER ET 
EFFECTUER REPARATION.
-BRANCHER PANNEAU CONTROLE SUR PRISE 120V POUR PERMETTRE DE 
CONTINUER A PROGRAMMER MALGRE LE PROBLEME.