-ENLEVER TUYAUX AIRFLOW SWITCH
-PERCER SHAFTS DES VENTILATEUR
-THREADER SHAFT DE VENTILATEUR AVEC TAP 1/2NC
-QTY: 6 ASSEMBLER SONDES \'SLIPSWITCH\' SUR WHIRLYJIG
-INSTALLER ASSEMBLAGE \'WHIRLYJIG\' SUR LES VENTILATEURS AVEC 
LOCKTITE ROUGE.
-TESTER 1 VENTILATEUR AVEC LE \'WHIRLYJIG\'.
IL SEMBLE AVOIR TROP DE VIBRATION SUR LE WHIRLYJIG POUR LA VITESSE 
DU VENTILATEUR.  IL FAUDRAIS QUE LES SHAFT SOIT PRE-PERCER SUR UNE 
TOUR OU BIEN D\'AVOIR UNE FACON FIABLE D\'EN FAIRE L\'INSTALLATION 
TRES PRECIS SUR LE CHAMPS POUR QU\'ELLE SOIT CENTRER A 100%.  AVEC 
DISCUSSION AVEC FGAUTHIER ET SLEGAULT IL EST DETERMINER QUE NOUS 
ALLIONS RE-INSTALLER DES TUYAUX 1/4 EN COPPE POUR FAIRE LE SWITCH 
DE DETECTION DE PRESSION D\'AIR.