NOTES : 
APPEL SERVICE GRAIN HANDLER : CLIENT N\'EST PAS CAPABLE REGULER LA 
TEMPERATURE.

APRES VERIFICATION, MODULE WATLOW ETAIS CONFIGURER EN % 
D\'OUVERTURE DE VALVE ET NON EN BOUCLE DE CONTROLE DE 
TEMPERATURE. CORRIGER PROGRAMMATION DU CONTROLEUR DE 
TEMPERATURE.

LAISSER 3 AIRSWITCH AU CLIENT A LEUR DEMANDE.

VEHICULES : 
DEPART 10H50
QUITTER 13H00