NOTES : AVEC SAMEUR (DEPART DE CASA 9H00RETOUR CASA 20H00)

INSTALLATION FILS SHIELDER POUR CORRIGER TROUBLE INTERFERENCE 
ELECTRIQUE POUR LES CAPTEUR DE CULOTTE DE L\'ELEVATEUR.

-INSTALLATION D\'UN CONDUIT LIQUIDTIGHT DE LA BOITE DE JONCTION 
HAUT DE L\'ELEVATEUR A LA BOITE DE JONCTION AU BAS DE L\'ELEVATEUR.
-FICHER 4X FIL SHIELDER A TRAVERS LIQUIDTIGHT. (RUN DE 90 PIEDS)
-FICHER LES FILS SHIELDER DE LA BOITE DE JONCTION AU BAS DE 
L\'ELEVATEUR JUSQUAU PANNEAU EZCONTROL.  IL A FALLU 4 TENTATIVE 
AVANT DE REUSSIR A LES PASSER.  (RUN D\'ENVIRON 140 PIEDS).
-BRANCHER LE FILLAGE DANS LE PANNEAU EZCONTROL ET AU CAPTEUR DE 
LA CULOTTE.
-TESTER LE SYSTEME, TOUT SEMBLE BIEN FONCTIONNER.

********
MATERIEL UTILISER A FACTURER SUR LE PROJET
INFORMATIONS ENVOYER A FCHEVRIER PAR COURRIEL.
1000 PIEDS FIL SHIELDER 1PR 18AWG
90 LIQUIDTIGHT500
2 CON-050-LQ