ARRIVER BUREAU: 6H00  (PREPARER TRUCK ET STOCK)
ARRIVER BUREAU: 16H50
DEPART DU BUREAU:17H00 (FAIRE RAPPORT)

-PREPARER TRUCK ET STOCK 

COMME JE LAVAIS MENSIONNER AU CLIENT VENDREDI PASSER SON AIR FLOW ETAIT GELER DU A LA TEMPERATURE EXTERIEUR QUI ETAIT DE -15 COMME LI LCIENT MA DIT

DANS LE BRULEUR IL A UN SENSOR DE TEMPERATURE QUI EMPECHE DE FAIRE PARTIR LE SECHOIR S\'IL FAIT TROP FROID A LEXTIEUR ALORS IL A RECHAUFFER SE SENSOR POUR FAIRE PARTIR LE SECHOIR MAIS LE AIR FLOW LUI ETAIT GELER COMME JAI DIT AU CLIENT MAIS IL VOULAIS ABSOLUMENT QUE JAILLE VOIR SON SECHOIR LUNDI MATIN MEME SI JAI DIT DATTENDRE QU\'IL FASSE PLUS CHAUD POUR SECHER

ALORS LORSQUE JE SUIS ARIVER SUR LE CHANTIER J\'AI REPLOGUER LE TUYAU DU AIR FLOW QUE LE CLIENT AVAIT DEPLOGUER POUR FAIRE MARCHER SON SECHOIR TEMPORAIREMENT ET TOUTE FONCTIONNAI CAR LA LE AIR FLOW N\'ETAIT PLUS GELER IL FAISAIS 1 DEGRES DEHORS

ALORS DEMANDER AU CLIENT SI IL AVAIT DAUTRE QUESTION ET JAI REPONDU A CES QUESTION ET NSUITE JAI VERIFIER QUE LE BRULEUR FONCTIONNE COMME IL SE DOIT 

LAISSER DES PIECE DE RECHANGE

  PIECE
THH-4179.......................(X1)
HH-1650.........................(X1)
HH-7063.........................(X1)
