NOTES :    VERIFIER SECHOIR
-VOIR SYSTEME DE REMPLISSAGE ACTUEL DU CLIENT ET PROPOSER 
QUELQUES SOLUTIONS PAR LOGIQUE RELAIS QUE SON ELECTRICIEN 
POURRAIS UTILISER POUR FAIRE FONCTIONNER LE SYSTEME.
-FS1 FERRAIS CLENCHER UN RELAIS 3PDT DONC ON FERRAIS PARTIR 
ELEVATEUR ET CONVOYEUR EN CONTOURNANT LE CONTACT DE MAINTIEN 
POUR SA STATION MARCHE ARRET, LE 3IEME POLE VA SERVIR COMME 
SIGNAL DE CONFIRMATION AU FILL SYSTEM.
-FS2 FERRAIS CLENCHER SA VIS DE REMPLISSAGE IL PEUT UTILISER UN 
RELAIS 2PDT, ON RETOURNE UN SIGNAL DE CONFIRMATION AU FILL SYSTEM 
ET ON CONTOURNE LE CIRCUIT MARCHE ARRET.
-POUR LE SIGNAL DU OVERLOAD, IL PEUT UTILISER LES CONTACT N.O. DES 
CONTACTEURS EXISTANT POUR FAIRE ALIMENTER UN RELAIS SI JAMAIS IL Y 
A SURCHAGE.  LE FILL SYSTEM UTILISERA LE CONTACT SEC N.F DE CE 
RELAIS POUR ENVOYER AU FILL SYSTEM