ARRIVER BUREAU: 14H10
DEPART BUREAU: 14H40
ARRIVER BUREAU: 22H50



-50 VOLTS SUR L1 DANS LE BOITIER DU BRULEUR
   -TESTER FIL DE COURANT (BON)
   -PAS PLUS DE COURANT DANS LE BOITIER DEMAREURE DU SECHOIRE
   ***FIL DU 120VOLT MAL BRANCHER ET A BRULER LE CONTACT AUXILKAIRE DU CONTACTEUR***

