NOTES : 
INSPECTION ELECTRIQUE ESA

INSPECTEUR: BILL WILSON 613-791-7319

LE SUIVANT DEVRAIS ETRE CORRIGER AVANT QUE L\'INSPECTEUR PUISSE RETOURNER ET DONNER UNE APPROBATION COMPLET:

ALIMENTATION:
LE DISCONECT QUI FOURNI L\'ALIMENTATION AU PANNEAU DE PUISSANCE DU SÉCHOIR EST SEULEMENT DE 200AMP CECI DEVRAIS ÊTRE CORRIGER ET REMPLACER PAR UNE SOURCE POUR ACCOMMODER LA CHARGE RÉEL DU SÉCHOIR QUI EST DE 215AMP, CECI DEVRA ÊTRE CORRIGER PAR L’ÉLECTRICIEN QUI A FAIT LA PORTION PUISSANCE.  L’ÉLECTRICIEN DEVRA ÊTRE CONTACTER A CE SUJET.

DOCUMENTATION:
-NAMEPLATE: LA CHARGE ELECTRIQUE SUR LE NAMEPLATE INDIQUE 300AMP, CECI DEVRAIS ÊTRE CORRIGER POUR BIEN IDENTIFIER LA CHARGE RÉEL DU SÉCHOIR QUI EST DE 215AMP
-LA LEVELING DRAG NE SE TROUVE PAS DANS LES SCHÉMAS ÉLECTRIQUE DE PUISSANCE, CECI DEVRAIS APPARAÎTRE A LA PAGE 4, A CORRIGER 
-NAMEPLATE: LE STANDARD DU TSSA EST 2016 ET NON 2012, A CORRIGER SUR LE NAMEPLATE.


PANNEAU DE PUISSANCE:
-UNE PLATEFORME DE MINIUM 1M DE LARGEUR DEVRAIS ÊTRE INSTALLER AU MÊME NIVEAU DE LA BASE DE BETON.  CECI DEVRAIS PERMETTRE DE TRAVAILLER DE FAÇON SÉCURITAIRE DANS LE PANNEAU (VOIR PHOTO).
-TOUT LES RELAIS DE CONTROLE DOIVENT ETRE BIEN IDENTIFIER DANS LE PANNEAU
-TOUT LES FUSIBLES DOIVENT ETRE BIEN IDENTIFIER DANS LE PANNEAU SELON LE PLAN (EX: FU1, FU2, ETC) AINSI QUE LEUR VALEUR NOMINAL (EX 2AMP, 10AMP, ETC)
-UN FUSIBLE OU DISJONCTEUR DOIT ÊTRE INSTALLER DIRECTEMENT APRÈS LE TRANSFORMATEUR DE CONTRÔLE EN SORTE DE PROTÉGER LE FIL DU COTER SECONDAIRE DU TRANSFORMATEUR LA VALEUR DE CECI DEVRAIS ETRE DE 10AMP, CET PROTECTION DOIS ÊTRE SITUÉE DANS LE MÊME PANNEAU.
-LES COMPOSANTES DOIVENT ETRE BIEN IDENTIFIER SUR LE FOND DU PANNEAU ET NON SUR LES GOULOTTES.

PANNEAU DE CONTRÔLE:
-LA PORTE DU PANNEAU DE CONTRÔLE QUI CONTIENS LES BOUTONS DE CONTRÔLE DEVRAIS ÊTRE MISE A LA TERRE.
-LE FILAGE QUI SE REND A LA PORTE DU PANNEAU, DOIVENT ÊTRE PROTÉGER D\'UN SPIRAL EN PLASTIQUE POUR PROTÉGER LES FIL.

PANNEAU DU BRULEUR:
-EMERGENCY STOP DEVRAIS ETRE IDENTIFIER.
-COLLANT LOCKOUT DEVRAIS ETRE IDENTIFIER SUR LE PANNEAU
-FIL QUI SERT A ALIMENTER FILL SWITCH, DEVRAIS ETRE REMPLACER PAR UN FIL TECK A LA PLACE DU FIL CAPTIRE EXISTANT.

PANNEAU AIRFLOW:
-COLLANT LOCKOUT DEVRAIS ETRE IDENTIFIER SUR LES PANNEAU

DRYER MASTER:
-BOUTON POUR ECHANTILLON DE GRAIN DEVRAIS ETRE BIEN IDENTIFIER.

CONDUITS DE FILAGE:
-IL FAUT FAIRE ATTENTION ET REPLACER QUELQUES FILS QUI SONT FIXER DE FAÇON A CE QUE LA GAINE DE FIL NE PEUT PAS SE COUPER CONTRE DES GARDES MÉTALLIQUES COUPANTES.  DES SUPPORTS DE PLUS PEUVENT ÊTRE RAJOUTER. (VOIR PHOTO)

PIECES : 


VEHICULES : 
REPAS (ENTRE 15H30 ET 16H00 EN ATTENTE DE L\'APPEL DE L\'INSPECTEUR ESA)
QUITTER 18H45