NOTES : * * * APPEL DE SERVICE GRAIN HANDLER.* * *

NE VEUT PAS PARTIR.

SECHOIR EN LPG, PAS ASSEZ DE PRESSION A L\'ENTREE CAUSE DE LA BASSE 
TEMPERATURE ET TANK PROPANE QUASIMENT VIDE, DOIS FAIRE REMPLIS.  
RECOMMANDE FORTEMENT UN POMPE POUR PROPANE LIQUIDE POUR EVITER 
DES PROBLEME DE GAZ EN BASSE TEMPERATURES.

RELAIS POUR LE BRULEUR ON ETAIS MAL ENCLENCHER DONC LA MODULATION 
NE SE FAISAIS PLUS, CORRIGER
