NOTES : 
SERVICE CALL PAR FGAUTHIER.
CLIENT DIT QU\'IL Y A FUITE DE GAZ SUR SYSTEME.
VERIFIER AVEC CLIENT.
-CLIENT SEMBLE DIRE QUE LE SECHOIR LAISSE PASSER LE GAZ DANS LE 
SECHOIR QUAND IL EST A L\'ARRET, LA FACON DONT LE CLIENT A TESTER 
CECI FAIT EN SORTE QU\'IL SERAIS IMPOSSIBLE QUE CECI SOIT LE CAS.  
VERIFIER ET LEAK TESTER LES DEUX TRAIN DE GAZ, AUCUNE FUITE 
DETECTER.
-CLIENT A DEJA FAIT VERIFIER A DEUX REPRISES PAR FDENIS INC. A DEUX 
REPRISES POUR VERIFIER LA LIGNE ET CECI EST ETANCHE AUSSI.
-LA SEULE POSSIBILITE QUI SEMBLE PLAUSIBLE EST QU\'IL Y A UNE RELEIF 
VALVE SUR LES DEUX BRULEUR QUI SEMBLE AVOIR PURGER DU GAZ PLUS 
D\'UNE FOIS, CECI PEUT ARRIVER SI PLUSIEURS ESSAIS POUR DEMARRER LE 
BRULEUR ET QU\'IL Y A DU LIQUIDE DANS LA LIGNE, SOIT SI IL Y A 
PLUSIEURS MIS-FIRE OU BIEN SI UTILISER EN MODE ON/OFF EN BASSE 
TEMPERATURE POUR CYCLER.


****
A VERIFIER AVEC FGAUTHIER SI ON REMPLACE OU NON LES DEUX RELEIF 
VALVE POUR SATISFACTION CLIENT

FACTURE # 440
VEHICULES : 
