NOTES : 

PANELVIEW SERIAL NUMBER:PVP41801
MODEL NUMBER : 2AFC-40155LM-P
SERIAL NUMBER : TD-17-32
MODEL NUMBER : 2AFC-40155LM-P
SERIAL NUMBER : TD-17-30

REPLACED PLENUM AND GRAIN TEMPERATURE 500 OHM RESISTORS WITH HIGH PRECISION RESISTORS
REPLACED PLC TOUCH SCREEN PROGRAM VERSION WITH VERSION 1.4
VERIFIED BURNER ORIFICE SIZE, TD-17-32 IS TO SPECIFICATION.
VERIFIED BURNER ORIFICE SIZE, TD-17-30 IS TO SPECIFICATION

PORTION CLIENT

MESURER FILAGE POUR RAJOUTER UNE STATION MARCHE ARRET, 100\' DE FIL TECH 16AWG6C EST REQUIS, EN PLUS DU 
BOITIER MARCHE ARRET, TYWRAP ET CONNECTEURS TECH

CLIENT DIT QU\'IL Y A UNE DE SES VIS DE DECHARGEMENT DE SILO QUI NE FONCTIONNE PAS ASSEZ VITE, IL FAUDRAIS SOIT 
GROSSIR LA POULIE DU MOTEUR OU REDUIRE LA POULIE DE LA VIS POUR AUGMENTER LA VITESSE, LE CLIENT DIT QU\'IL A A 
UN TOMMY QUI EST DEJA PASSER ET AUSSI RICHARD CHAUMONT A UN AUTRE MOMENT

BESOIN D\'UN OVERLOAD POUR MOTEUR 10HP POUR PANNEAU MULTICO

INSTALLER ET CONFIGURER WATCHDOG, MESSAGERIE WATCHDOG FONCTIONNE, PAR CONTRE VNC VIEWER NE FONCTIONNE 
PAS A DISTANCE, JE CROIS QU\'IL S\'AGIT PROBABLEMENT DE PORT BLOQUER CHEZ LE FOURNISSEUR INTERNET VIDEOTRON.  
J\'AI VIDEOTRON A LA MAISON ET JE VAIS FAIRE UN ESSAI A LA MAISON AVEC UN PANNEAU POUR CONFIRMER SI C\'EST LE CAS.


A FACTURER 1X MOD-H-SECH
PIÈCES : 
S102C500R0000.01% QTY: 5

ROUTER TOP DRY QTY:2 (ROUTER DLINK A FACTURER CLIENT)

DEPART 7H40 CHEZ CASA VUE AVEC FRED G.
ARRET AU BUREAU RAMMASSER PIECES ET REMPLIR PROPANE.