CLAIM FOR TOPDRY AUTOFLOW PLC SYSTEMS SOLD AND INSTALLED DURING THE 2017 SEASON

WE ARE VERIFYING THE FOLLOWING FOR THE CLAIM

REPLACEMENT OF 1/4W 500OHM RESISTORS : 
THE RESISTORS INSTALLED WITH THE PLC UNITS ARE NOT PRECISION RESISTORS.  THE FUNCTION OF THE RESISTORS IS TO 
ACT AS A REFERENCE MEASUREMENT FOR THE TEMPERATURE SENSORS.  IF THE REFERENCE MEASUREMENT IS NOT IDENTICAL 
BETWEEN SENSORS IT WILL THROW OFF THE TEMPERATURE CURVES BETWEEN THE SENSORS CAUSING A DIFFERENTIAL 
TEMPERATURE TO OCCUR.  SIMPLY ADJUSTING AN OFFSET IS NOT A VIABLE OPTION AS THIS WILL ONLY CORRECT 
TEMPERATURE AT A CURRENT GIVEN TEMPERATURE AND NOT CORRECT THE CURVE AS NEEDED.  IN ORDER TO CORRECT THE 
ISSUE THE 1/4W RESISTORS ARE REPLACED BY HIGH PRECISION 500OHM RESISTORS HAVING A TOLERENCE FOR ERROR OF 
+/-0.01% WHICH IMMEDIATELY CORRECTS THE ISSUE, THIS WAS TESTED ON 3 SITES DURING FALL OF 2017 AND COMPLETELY 
RESOLVED THE DIFFERENTIAL TEMPERATURE ISSUES.  AS A RESULT WE WILL REPLACE THE RESISTORS DURING OUR CLAIM
THERE ARE SOME PHOTOS AVAILABLE OF THE IMPACT OF REPLACING THE RESISTORS, THERE WILL BE ONE OR TWO SITES OF 
THIS AS AN EXAMPLE


UPDATE OF THE PLC PANELVIEW SOFTWARE FROM VERSION 1.3 TO VERSION 1.4
AS PER COMMUNICATION WITH ANDRES COLLADO 12-DECEMBER-2017, IN ORDER FOR THE WATCHDOG SYSTEM TO BE 
CAPABLE OF SENDING OUT EMAILS OR SMS\' TO WARN THE CUSTOMER THAT THE DRYER HAS STOPPED FUNCTIONING THE 
UPDATE OF THE SOFTWARE IS MANDATORY.  VERSION 1.3 FAILS TO SEND OUT SMS OR EMAIL, AS A RESULT WE WILL UPDATE 
THE SOFTWARE VERSION.
WE WILL TAKE A PHOTO OF THE PANEL SERIAL NUMBER WITH VERSION THAT WAS INSTALLED ON SCREEN


VERIFICATION OR ORIFICE SIZE ON ALL LPG BURNERS.
WE HAVE HAD DURING THE 2017 SEASON, A FEW BURNERS THAT DID NOT PERFORM TO INDUSTRY STANDARD AND DID NOT 
PERMIT THE PLENUM TO ATTAIN PROPER DRYING TEMPERATURES, ALTHOUGH THIS DOES NOT SEEM TO BE AN ISSUE THAT 
REOCCURS OFTEN AND WOULD ONLY BE AN ISSUE ON SYSTEMS WITH ONLY ONE BURNER WE WILL VERIFY THAT THE ORIFICE 
SIZES ON THE GAS TRAINS ARE ALL TO SPECIFICATION OF 0.344\'\'.  IN THE EVENT THAT THE ORIFICE IS UNDERSIZED TWO 
PHOTOS WILL BE TAKEN TO SHOW THE MEASUREMENT AT DIFFERENT ANGLES AND THE ORIFICE WILL BE RESIZED TO 0.344\'\'

CLAIM-90023 : 602.10$ FRANCOIS PAQUIN ET FILS
CLAIM-90024 : 436.10$ FERME M. MYRE
CLAIM-90025 : 436.10$ FERME JAQUES LEDUC ET FILS
CLAIM-90026 : 490.85$ LAURENTIA FARMS
CLAIM-90027 : 505.10$ CRIBLAGE MARC BERCIER
CLAIM-90028 : 421.85$ P ET H KOCH FARMS
CLAIM-90029 : 421.85$ JEAN DANIEL KIRBY
CLAIM-90030 : 436.10$ FERME NADO HENDERSON
CLAIM-90031 : 436.10$ FERME RICHER
CLAIM-90032 : 436.10$ FERME GRAIN D’OR
CLAIM-90033 : 643.10$ CULTURE CEREALIERE LAPOINTE
CLAIM-90034 : 643.10$ FERME MJ FILLION 
CLAIM-90035 : 830.10$ FERME CLAUNIC
CLAIM-90036 : 681.60$ FERME P.E. POULIOT
CLAIM-90037 : 436.10$ FERME CLAUDE ISABELLE ET FILS INC.
CLAIM-90038 : 505.10$ FERME DES ILETS 2003 INC
CLAIM-90039 : 505.10$ COVILAC
CLAIM-90040 : 505.10$ FERME WALSER INC.
CLAIM-90041 : 436.10$ FERME GUYROJOY (2008) INC
CLAIM-90042 : 436.10$ FERME VILLIARD ET FILS INC
CLAIM-90043 : 436.10$ FERME COLLETTE ET FILS