NOTES : APPEL DE SERVICE POUR BRULEUR TOP DRY GAZ NATUREL.
DIAGNOSTIQUE : BRULEUR USAGER CONVERTI POUR SYSTEME PLC.  NE 
VEUT PAS DEMARRER.
-VERIFIER DANS L'ECRAN NE PEUT PAS PARTIR CAR LES CONDITIONS 
N'ETAIS PAS ATTEINT.  METTRE ''DISABLE'' LES ROTOBINES DE TOIT POUR 
PERMETTRE DE PARTIR LE SECHOIR.
-UNE FOIS PARTI, LE VENTILATEUR AVAIS ROTATION INVERSER, CORRIGER.
-AIR FLOW SWITCH INVERSER AUSSI, CORRIGER.
-LE REGULATEUR DE GAZ N'ETAIS PAS INSTALLER SUR LE SECHOIR ENCORE 
DONC IMPOSSIBLE DE FAIRE UN TEST FIRE AVEC LE GAZ, MAIS QUAND 
MEME FAIT UNE SIMULATION, TOUT SEMBLE OK.

******
NOTE IMPORTANT:
LA PLAQUE SIGNALITIQUE SUR LE BRULEUR N'EST PAS LISIBLE, IL FAUT QUE 
LE CONTRACTEUR DE GAZ PUISSE INSCRIRE LE NUMERO MODELE, NUMERO 
SERIE DE L'APPAREIL DANS SES DOSSIERS AU DEMARRAGE, SURTOUT POUR 
UN APPAREIL GAZ NATUREL.  IL N'EST PAS IMPOSSIBLE QUE LE DEMARRAGE 
DE L'APPAREIL SOIT REFUSER PAR ENERGIR DUE A CECI, DANS CE CAS IL 
FAUDRAIS ETRE EN MESURE DE PRODUIRE UNE PLAQUE DE REMPLACEMENT 
OU REMPLACER L'EQUIPEMENT.
*******
