NOTES : 
INSPECTION CSA POUR SECHOIR GRAIN HANDLER.

-CORRIGER FIL MISE A LA TERRE POUR PORTE DE PANNEAU.

***NON-CONFORMITE AU NIVEAU DE L\'ALIMENTATION DE GAZ AU SECHOIR.  
PLUSIEURS BALL-VALVES DE TROP (JUGER PAS NECESSAIRES) DE PLUS IL 
N\'Y A AUCUN SOUPAPE DE SURPRESSION ENTRE LES DITES BALL-VALVES 
POUR PROTEGER LA LIGNE LIQUIDE DANS LE CAS 
D\'EXPANSION/SURPRESSION DU PROPANE LIQUIDE.  BUDGET PROPANE A 
ETE APPELER ET AVISER, IL SONT SUPPOSER DE CORRIGER LEUR 
INSTALLATION.***

VEHICULES : 

DEPART 9H15