NOTES :* * *  APPEL DE SERVICE PAR FGAUTHIER * * * 
DIAGNOSTIQUE : CLIENT SEMBLE PENSER QUE LE PROBLEME EST LE HI-
LIMIT TRANSISTION DU BRULEUR (BRULEUR CHI-TOWN)

VERIFICATION DU SYSTEME :

-TRANSISTION HI LIMIT SEMBLE ETRE EN BON ETAT, BONNE CONTINUITE 
PAS DE FIL DE LOOSE.

-SELON EMPLOYE  IL Y AURAIS UN PROBLEME POUR ALIMENTER LE SYSTEME 
LES RELAIS FONT PARFOIS DES ''FREEGAME'' AU DEMARRAGE.  PAR CONTRE 
LE RELAIS 12VDC EST ALIMENTER A LA SORTIE DU PLC QUI ALIMENTE 
ENSUITE UN AUTRE RELAIS 24VAC QUI LUI ENSUITE ALIMENTE LE 
CONTACTEUR POUR FAIRE PARTIR LE VENTILATEUR DU SYSTEME.  
REMPLACER LE RELAIS 24VAC (A LA DEMANDE DU CLIENT)  (JE N'AVAIS PAS 
DE RELAIS 12VDC DISPONIBLE POUR REMPLACER CELUI A LA SORTIE DU 
PLC)  MAIS EXPLIQUER AU CLIENT QUE SI LE PROBLEME PROVIENS DE LA 
SORTIE DU PLC C'EST NORMAL QUE TOUT CE QUI SUIT VA AVOIR LE MEME 
PROBLEME.
-REMPLACER LA TRANSISTION HI-LIMIT (A LA DEMANDE DU CLIENT) (PIECE 
FOURNI PAR CASA FGAUTHIER)
-EMPLOYEE DISAIS ENSUITE QUE LA TEMPERATURE HI-LOW CYCLAIS PAS 
CORRECTEMENT.  LE SYSTEME FONCTIONNE CORRECTEMENT AVEC LE 
THERMOSTAT DIGITAL, IL Y A UN RELAIS ADDITIONEL EN SERIE AVEC, 
PROVENANT DU SYSTEME DU CLIENT POUR AUSSI FAIRE CYCLER HI-LOW.  
J'AI EXPLIQUER A L'EMPLOYEE QUE LA TEMPERATURE HI-LOW DOIS ETRE 
AUSSI REGLER PAR LE SYSTEME DU CLIENT.
-SINON, IL NE SEMBLAIS VRAIMENT PAS VRAIMENT AVOIR DE PROBLEMS 
AVEC LE BRULEUR DU CLIENT