NOTES : * APPEL DE SERVICE SECHOIR
- DIAGNOSTIQUE PROBLEME D'ALLUMAGE BRULEUR NO 2
- REMPLACEMENT DU FILLAGE IGNITION
- REMPLACMEMENT DE LA CARTE FENWAL
- REMPLACEMENT CONDUCTEUR CORRODER 
- REMPLACEMENT DE L'IGNITER
- REPARATION DU CONDUCTEUR DU CYCLE VALVE
- TEST DES FEUX
* VENTE DE MATERIEL DE CAM-REQUIS103
  - 1* THH-4178
  - 6* WR-7MM-BOUGIE
  - 1* HF-4624-R