NOTES :   REMISE EN FONCTION TOUR SECHOIR

-NETTOYAGE PANNEAU DE CONTROLE PRINCIPALE, ENLEVER FILAGE ET 
MODIFICATIONS NON-STANDARD A L'APPAREIL.

-ENLEVER LE HGP ET LGP DEFECT
-INSTALLER UN LGP SWITCH (INVENTAIRE SCOURNOYER, DOIS RECUPERER 
DE CASA LORSQUE PIECE DEVIENS EN STOCK)

-ENLEVER RESTANT DE CONDUIT LIQUID TIGHT ENDOMAGER.

-INSTALLER BOITE DE JONCTION, DIN RAIL ET TERMINAUX. POUR TOUT LES 
PIECES SUR LE TRAIN DE GAZ

-INSTALLER NOUVEAU LIQUIDTIGHT POUR LES COMPOSANTES DU TRAIN DE 
GAZ.

-REMPLACER VAPOR HIGH LIMIT, DEFECTUEUX.

-TESTER LES GAUGES A PRESSION, TOUT TEST OK MAIS CELUI 0-15PSI 
PEUT ETRE A REMPLACER.

-ENLEVER FITTING AVEC KIT DE TORCHE POUR ETRE CAPABLE D'INSTALLER 
BON FITTING POUR UV SENSOR.

-FORMULER UN PLAN DE MATCH AVEC S.AMEUR ET S.BERGERON POUR LES 
TRAVAUX A COMPLETER.  FIL UV, FIL IGNITION, ROTOBINE DE TOIT, 
CONDUIT POUR LA ROTOBINE, INLET SENSOR, ETHERNET ET PANNEAU DE 
CONTROLE.

-JE COMPLETERAIS LES BRANCHEMENTS A LA PROCHAINE VISITE.
****
NOTE : CLIENT AVAIS ETE AVISER QU'IL ETAIS RECOMMANDER DE FAIRE 
RACCORDER GAZ ET ELECTRICITE SUR LE SECHOIR POUR PERMETTRE 
QU'ON TEST L'APPAREIL UNE FOIS LA REMISE EN FONCTION EST 
COMPLETER, CECI N'A PAS ENCORE ETE FAIT.