VERIFIER AIR FLOW SUR BURELEUR CAR LA CARTE FENWALL ETAIT PAS ALIMENTER. AIR FLOW FONCTIONNAIS PAS IL AVAIT 
PAS SON CONTACT QUI FERMAI 
       -VERIFIER 120VOLT SI IL SE REND AU AIR FLOW 
       -VERIFIER SI CONTACT LE 120VOLTS PASSE (NON)
       -VERIFIER SI TUYAUX D\'AIR N\'EST PAS BLOQUER PAR QUELLE QUE CHOSE (NON) 
       -VERIFIER SANS DE ROTATION DE LA FAN CAR JAVAIS UN PETIT DOUTE ENSUISTE LE CLIENT MA DIT QUIL A CHANGER LE 
        MOTEUR RESSSAMENT ALORS VERIFER ET ELLE TOURNAIS A LENVER ALORS CHANGER LE SENCE DE ROTATION DU 
        MOTEUR. LORSQUON A CHANGER LE SENCE ON NE TROUVAIS PAS LA PLAQUE QUI INDICAIT LES TAPE ALORS LE CLIENT A 
        DIT OUI CEST 5 ET 8 QU\'IL FAUT CHANGER MAIS JE NETAIT PAS SUR MAIS LE CLIENT ETAIT BIEN SUR DE LUI ET JE LES 
        AVERTI QUI SI QUELLE QUE CHOSE BRISE JE NE SUIS PAS RESPONSABLE IL MA BIEN CONFIRMER QUE SI QUELLE QUE 
        CHOSE BRISE SCEST LUI (ALOSR UN CONDANSATEUR A BRISER) ENSUITE LE CLIENT A DECIDER D\'APPELLER LE GARS QUI 
        A REFAIT SON MOTEUR POUR LUI DEMANDER QUOI INVERSER COMME FIL POUR FAIRE CHANGER LA ROTATION DU 
        MOTEUR ENSUITE CHANGER CONDENSATEUR ET RETESTER BRULEUR ET FONCTIONNE BIEN.