NOTES : TROUBLE AVEC SECHOIR DEPUIS VENDREDI
- PAS FACTURABLE
- CHANGER TRANSFO 
- CHANGER BREAKER SORTI TRANSFO
- INSTALLER RELAIS ENTRE DRYER MASTER ET SECHOIR
- DEPLACER SONDE HI-LIMITE
- AJUSTER PRESSION
RESTE A FAIRE
- CHANGER HI-LIMIT GAZ POUR UN QUI VAS JUSQU\'A 50WC
- RAJUSTER PRESSION POUR AVOIR 16M BTU/H
- CHANGER CONTROLEUR HI-LIMIT CAR IL ES AJUSTABLE SEULEMENT 
JUSQU\'A 121 C ALORS QU\'ONT SECHE A 125 C
- DEPLACER LOW GAS 