NOTES : 
DEMARRAGE TOP DRY
-MANQUE CABLE ETHERNET ENTRE PANNEAU HMI ET PLC, RAJOUTER OK
-ROTOBINE LOW LEVEL, MAL INSTALLER, COTTER PIN ACCROCHE DANS 
TUYAUX, DOIS DEBRANCHER ENLEVER DESASSEMBLER, ET TOUT 
REINSTALLER LA ROTOBINE.
-ROTOBINE OVERFLOW SUR CONTACT NO A PLACE DU NC
-MANQUE JUMPER SUR TERMINAL 9 POUR GAS SWITCH DANS BRULEUR.
-RESISTANCE DE LOOSE POUR PLENUM TEMPERATURE CAUSANT UNE 
MAUVAISE LECTURE DU PLENUM
-AJUSTER FLAME PROBE BRULEUR 1 CAR IL TOUCHE AU FRAME
-CORRIGER BRANCHEMENT 120V DU BRULEUR
-ENLEVER SOURCE 120V SUR PANNEAU PLC PROVENANT DU EZCONTROLE 
(ELECTRICIEN DIT AVOIR POSER LA QUESTION A UN TECH DE CASA ET QU\'IL 
L\'ONT DIT QU\'IL FALLAIS ENVOYER LE 120V A PARTIR DU EZCONTROLE, A 
VERIFIER)
-CORRIGER USER SAFETY POUR PANNEAU SECHOIR A TRAVERS LE 
EZCONTROLE, UTILISER LE CONTACT L2, T2 DU MCR POUR SE FAIRE.
-AJUSTER STOPSWITCH SUR ELECATEUR.
-CORRIGER DELAIS DEMARRAGE POUR CONVOYEUR QUI FEED ELEVATEUR 
PASSER DE 0.1SEC AND 6 SECONDES DE DELAIS
-CORRIGER ERREUR DANS LE BRANCHEMENT DU EZ CONTROLE QUI 
BYPASSAIS LE CYCLE DE DEMARRAGE ET ALIMENTAIS LA VIS DE 
REMPLISSAGE HUMIDE SANS DEMANDE ET QU\'EN DEMANDE ALIMENTAIS 
SEULEMENT LE CONVOYEUR DE RECEPTION.
-PARTIR ET AJUSTER BRULEUR
-EFFECTUER FORMATION DU SYSTEME AU CLIENT
-SECHER QUELQUES BATCH AVEC LE CLIENT ET REPONDRE AU QUESTIONS.
